Photovoltaic Cable, Power Cable, CU/XLPE (UL 44/ICEA S-95-658/NEMA WC70)
Rated and listed as PV Wire per UL. Also listed as Type USE-2 and RHH / RHW-2. All sizes are rated VW-1, Gas & Oil Res. I or II and Direct Burial. Rated Sun Resistance in all colors, and CT Use, 1/0 AWG and larger. Rated RW90/RWU90 per UL. c(UL)us. Meets vertical flame tests. 18 and 16 AWG rated as PV only
For interconnection wiring of grounded and ungrounded photovoltaic power systems as described in Wiring Systems, Article 690, and other applicable parts of the National Electrical Code (NEC), NFPA 70.
UL Subject 4703 Outline of Investigation for Photovoltaic Wire.
Service Entrance Cables.
Rubber-Insulated Wires and Cables, for cables rated RHW-2 or RHH.
ICEA S-95-658/NEMA WC70
Non-shielded 0-2 kV Cables.
Maximum operating voltage: 600 V, 1000 V or 2000 V
Maximum conductor operation temperatures: 90 °C wet and dry
1. Conductor: Soft annealed uncoated copper Class B compressed or unilay compressed per ASTM B8 or Aluminum AA-8000 alloy compacted conductor, Class B stranding, per ASTM B801.
2. Binder Tape: A suitable opaque tape, as required.
3. Insulation: Black thermoset flame retardant cross-linked polyethylene (XLPE). On request, other colors